Can immersion sleeves be installed in the heating group, in order to measure the temperatures for heat quantity measurement?
The immersion sleeve of the product range with 30 mm is suited for this. This immersion sleeve is generally installed in the flow ball valve. However, only one immersion sleeve can be installed per heating circuit because otherwise, the space within the heating group would not be sufficient. The second point for temperature measurement is generally integrated on the return side of the heat flowmeter.